So far,...... with the extreme changes in OAT temp we've had in the past week, it's changes in draft strength that have been doing a better job of regulating the stove than I have byexperimenting with the primary adjustments.
Seems there's not as much change needed in primary damper opening size as I'm used to needing with the range.
The #6 is a large, forgiving brut compared to the small firebox of the range.
- Sunny Boy
- Posts: 13778
- Joined: Mon. Nov. 11, 2013 1:40 pm
- Hand Fed Coal Boiler: Anthracite Industrial, domestic hot water heater
- Baseburners & Antiques: Glenwood range 208, # 6 base heater, 2 Modern Oak 118.
- Coal Size/Type: Nuts !
- Other Heating: Oil &electric plenum furnace
- Location: Central NY