This forum is for common products and questions such as chimney installations, CO detectors, coal bin designs and a variety of other general topics that do not fit into the other forums.
2 posts • Page 1 of 1
- Posts: 26
- Joined: Thu. Dec. 20, 2012 5:31 am
- Stove/Furnace Make: Alaska
- Stove/Furnace Model: Channing III
- Location: Allegany, NY
My stove has a rear vent. I have a 1 ft. pipe off the back hooked to a 90 then a 2 ft. section up hooked to the damper into another 2 foot section to a cut section about 1.5 foot to another 90 hooked to the powervent. My question....should I move the damper down to hook to the elbow then put the 2 ft. section above or is it ok the way it is? It seems I have read the recommendation is to hook the damper right into the 90 at the bottom. Will my current set up cause any problems? Thanks in advance for any insight!
- Posts: 6009
- Joined: Sun. May. 02, 2010 11:26 pm
- Stoker Coal Boiler: AXEMAN-ANDERSON 130 "1959"
- Coal Size/Type: PEA / ANTHRACITE
- Other Heating: Ground Source Heat Pump
- Stove/Furnace Make: Hydro Heat /Mega Tek
- Location: Junction of PA-OH-WV
The way you have it is best.
SLOW AND STEADY WINS THE RACE